PUMPING SYSTEM CURVE
The main topics:
The definition of "Pumping system".
Characteristics of the Pumping System.
Static head of the pumping system.
Dynamic losses in the pumping system.
4.1. Friction Losses in the pipelines. Fluid velocity. Bernoulli equation.
4.2. Losses in valves, filters, etc.
5. Pumping system with mainly static head.
6. Pumping system with mainly dynamic component.
The pump perform the following work:
1. Lifting the liquid on the height Hg
2. Overcoming the pressure difference in tanks 1 and 2 . If the tanks are open in atmosphere difference is not taken into account.
3. Pushing the liquid through pipelines, gate valves, filters pipe bends etc, .
What is necessary to know about the piping system characteristic for the correct pump selection?
The clear understanding of systems characteristic is the necessary condition for the right pump selection and efficient pump operation.
The piping system characteristic has two parts - static head and friction losses.
The system offers resistance to the flow in two ways that are fundamentally different. The work to lift anything is mgh where m is the mass lifted, g is the gravitational constant and h is how high the mass was lifted. The pump sometimes lifts fluid and it always has to overcome frictional forces. These two types of work are fundamentally different and has to be dealt with in different ways. The pressure to overcome when lifting the fluid equals the pressure difference between the pump and the outlet from the system with zero flow. It is the pressure that would be measured at the pump using a pressure gauge or the height of the fluid at the outlet minus the height where the pump is.
Pressure Resistance of a System
It takes energy to lift fluid from one level to another
The pressure used to lift fluid is called Static Head
The energy used to lift fluid is independent of velocity
It takes energy to move fluid through a system of pipes and other equipment.
The pressure used to overcome friction is called the or Dynamic Friction Head.
The pressure required is proportional to the square of the fluid velocity
The power is proportional to the cube of the velocity
Static head Hstat includes geometrical height where the liquid has to be lifted and differences in pressures above liquid surfaces in intake reservoir and pressure reservoir.
Dynamic losses or Frictional losses (Hf) include friction losses in pipes valves, pipe bends, filters head exchangers etc all elements where the flow changes its shape, direction.
Headloss (Hf) is the loss of energy due to the friction of the piping materials and is expressed in meters of head. This can be determined theoretically using The Darcy Weisbach Equation.
Pipe friction loss estimates are based on an equation referred to as Darcy-Weisbach
This equation is very useful to examine to understand what parameters influence frictional losses in piping:
Hf - pressure drop due to friction (ft or m)
f - Darcy friction factor
L - pipe length (ft or m)
d - pipe diameter (ft or m)
V - velocity head (ft or m)
k - coefficient which depends on the element characteristic.
Q - is a flow goes through the elements
The friction head loss:
- Function of fluid velocity
- Lower flow (lower velocity) results in lower head loss
- Head loss is proportional to the square of velocity
- Reduced to 25% when velocity is cut in half !
- Increases by a factor of 4 when velocity is doubled
Depending on what share the static head and friction losses have in overall the system curve systems can be separated on systems with preliminary static head and preliminary friction losses.
Pump System curve.
System with mainly static head
System without static head. Only friction losses are presented.
How to build the system curve?
The graphical presentation is the most obvious way to understand the characteristics of a piping system and the influence of every element on the overall characteristic.
Serial hydraulic resistances.
To calculate the overall losses in the pipeline with serial resistances it is necessary to summarize resistance of every element.
These are the steps
Draw curves of each element of a piping system, valves, pipes connections, pipe bends, etc.
If elements are connected in series the same flow goes through every element. It means that for building a system curve it is necessary to add the head of every element at the same flows.
If a piping system has parallel branches the flow is divided but the values of pressure at the common points will be the same.
In this case, the summarized system characteristic will be received by adding characteristics of branches at the same head.
Draw the summarized curve of a pumping system.